Transformer oil testing is a key part of any preventive maintenance program and should be conducted on a regular basis. It is an early warning system that helps you set priorities before they become emergencies.
The following are some of the most common tests for transformer oil:
An annual Dissolved Gas-In-Oil Analysis (DGA) is the most important test for transformer oil and can give an early indication of abnormal conditions. As the name describes, this test analyzes the type and quantity of gases dissolved in the oil, using a small sample that is examined in a laboratory. Certain quantities and combinations of gases typically found in the oil can indicate insulation overheating/overloading, liquid overheating, partial discharge (corona) or arcing in the transformer.
The screen test is a collection of physical, electrical, and chemical tests for transformer oil. Typically, a 1 liter sample of oil is collected. No single test alone will indicate the true condition of the liquid, so it is suggested all be performed. The group of tests include:
The water content test detects the moisture content in parts per million of the liquid insulation. A test to determine polychlorinated biphenyls (PCBs) on a percentage value or as a parts-per-million value is available.